NYC MC 810.3 Smoke test
To determine the tightness of chimney construction, a smoke test shall be made in accordance with the following conditions and requirements:
- The equipment, materials, power and labor necessary for such test shall be furnished by, and at the expense of, the owner or holder of the work permit.
- If the test shows any evidence of leakage or other defects, such defects shall be corrected in accordance with the requirements of this chapter, and the test shall be repeated until the results are satisfactory.
- The chimney shall be filled with a thick penetrating smoke produced by one or more smoke machines, or smoke bombs, or other equivalent method. As the smoke appears at the stack opening on the roof, such opening shall be tightly closed and a pressure equivalent to 1/2-inch (13 mm) column of water measured at the base of the stack, shall be applied. The test shall be applied for a length of time sufficient to permit the inspection of the chimney.
What Our Customers are Saying…
Thank you for the recent work your company completed on my chimney cap. You spent a good deal of time to correct a long standing smoke problem I had in my chimney fireplace. By installing a custom made chimney cap and flue system my problem has been resolved. I thank you for the professional quality work the timely manner in which it was completed and will not hesitate to refer you to friends who might need your services.